Product Selected: DL205
Category Selected: Analog
Press "Ctrl-F" to search for specific words in this FAQ.
|Question: Is Pointer addressing prohibited for analog modules located in Remote bases?|
| Answer: Yes - you cannot use the pointer method in remote bases that have analog cards.
|FAQ ID: 66|
|Question: Can you use an F2-04THM and another analog module in a local DL-205 PLC system?|
|FAQ ID: 85|
|Question: Is the analog setup for D2-250, D2-250-1 or D2-260 pointer method the same as for D2-240?|
|FAQ ID: 86|
|Question: Does your line of EBCs support thermocouple input modules?|
| Answer: Yes.
|FAQ ID: 592|
|Question: Is a D2-230 capable of analog inputs?|
| Answer: A: Yes you may use analog inputs with the D2-230.
|FAQ ID: 787|
|Question: What are the color codes for American/Canadian thermocouples?|
| Answer: All American/Canadian Thermocouples follow the ANSI color standard for wire coloration. Jacket color may sometimes be the main wire color, but it is not a dependable means of thermocouple type.
Type J - White/Red
Type E - Purple/Red
Type K - Yellow/Red
Type T - Brown/Red
Type N - Orange/Red
Red is always Negative.
|FAQ ID: 1307|